In the Racine area, First Call Heating & Cooling, Inc. is well known for providing exceptional furnace repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with First Call Heating & Cooling, Inc. because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in South Milwaukee, WI. Call us today at (262) 634-9025!
I was very impressed with Joel's work. He was on time, quick and thorough.
the team at First Call did a great job working with us and honoring the 5 year warranty. They are very pleasent to work with. I would have liked more frequent updates on the backordered part, but that was a minor issue.
Just performed a service on a carrier mid efficiency furnace
Checked thermostat and verified operation, checked air filter, cleaned condensate, cleared drain lines, inspected burners and heat exchanger, cleaned intake pipe, cleaned flame sensor, checked ignitor, checked blower and inducer motor amperage, checked gas pressure, checked temperature rise, checked all wire and electrical connections, and cleaned unit. Unit running and heating well!
Upon arrival found unit running very low pressures and tripping out on low pressure switch, verified fan setting correct and filter clean. Unit likely low on refrigerant, cannot verify this or add due to evap coil full block of ice. Superheat very low at 4°, subcooling near correct at 8/10. Pressures 60/270, herm amp very low at 5.0, indicating restriction due to ice (charge) or TXV. Informed homeowner of issue and will need to reschedule when thawed. Left furnace off and condenser off. Customer paid diagnostics and min. Labor
Performed an ac start up
Installed a new AC system.
Quoted customer 2 new AC systems.
Customer bought a 16 seer AC system.
Trane furnace tuneup, maintenance, and inspection. Checked thermostat, cleaned condensate trap, checked air filter, cleared drain lines, cleaned flame sensor, checked igniter, inspected burners and heat exchanger, checked and cleaned intake pipe, checked blower and inducer motor amps, checked and adjusted gas pressure, checked all wire and electrical connections, checked temperature rise, and cleaned unit. System running and heating well!
Customer bought a new AC system.
Quoted customer a 16 seer AC system.
Diagnosis and repair of a dirty flame sensor in a Bryant furnace.
Air conditioning repair
Carrier Furnace repair and cleaning. Goodman central air will be checked in spring for cooling operation. AO Smith water heater in good working order.
Natural draft furnace inspection, First Call heating and cooling
Humidifier repair, first call heating and cooling, 24/7 service and emergency repair
Quoted customer a Trane AC system.
Rheem air conditioning repair
Quoted customer a Trane single stage furnace and 13 seer AC unit. Looking to add second system in his addition.
Bryant furnace not heating. Main circuit board not bringing blower on.