Since 1995, First Call Heating & Cooling, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the Racine area. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that First Call Heating & Cooling, Inc. stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Racine, WI. Call us today at (262) 634-9025!
Nice service person
I've been using First Call for many years now because their fair prices come with knowledgeable, thorough, prompt & courteous techs. During our recent subzero cold snap my furnace went out and even though it was 3am and the techs were working around the clock, one of them called me within 5 minutes and told me what I could try to get it going. Sure enough it worked! Just flat out a great local company!
Very good service
Tyler was a good technician, gave me details on my furnace and was very professional!
Great service, pleasant technician and reasonable price.
Understood what was needed, wasted no time, fixed our issues
Tyler called and said he would be a bit late which was no problem for us. He did arrive and properly introduced himself. After reviewing the problem, he popped off the cover of the humidifier and discovered a hose was disciinected. After reattaching it, everything was good. He reviewed the operation with both my wife and me. Current humidity levels are good. Tyler is a very pleasant young man and a very professional tech. Thanks again First Call staff.
Great service- more expensive than expected
Very curtious and very helpful showed up earlier than exspected
Joel Vern was cordial, professional and mechanically proficient in getting task completed.
I've been dealing with First Call from some years now for all my heating and air conditioning needs. They are always expert, reliable, and professional. A great company!
I was so happy to open the door to a female technician. We need more in these fields. I give Lauren an A+’
Carrier furnace flame rollout switch tripping furnace off caused by a plugged secondary heat exchanger. Unit also has an inducer motor with bearings that are grinding. Recommended replacement of furnace vs repair due to age and condition, customer is rescheduled for a free estimate and left space heaters for a temporary source of heat today!
Quoted customer to install new duct work.
Quoted customer a modulating furnace with 16 seer AC system.
Return call to replace circuit board on a carrier furnace that had a melted relay causing heat not to to cycle. Replaced board and verified operation, system is now running and heating well again with proper temperature readings and amp draws! No further issues with furnace to report !
Customer bought a new heating and cooling system.
Quoted customer a new hi-efficiency furnace.
Trane furnace not heating due a shorted limit safety switch most likely failure cause was due to a plugged air filter causing excessive trips over a length of time causing failure of switch. Replaced filter and ordered a new switch, we are rescheduled for part replacement. Left a space heater meanwhile for a temporary source of heat.
Goodman 80% furnace not heating, inducer motor getting amperage but not starting. On further inspection found a bad run capacitor attached to inducer, replaced part and verified operation. Also adjusted gas pressure and swapped filter, no further issues to report!
Water heater repair and replacement
Just completed a maintenance agreement furnace tune up on a Trane S9V2, Checked thermostat and verified operation, checked and replaced Honeywell filter, checked intake pipe, cleaned flame sensor, cleared drain line, checked ohms on the igniter, inspected heat exchanger, checked gas pressure low and high fire, checked amperage on blower and inducer motor, took a temperature reading on return and supply, checked all wires, cleaned unit, everything is running great!
Just completed a maintenance agreement tune up on a Goodman furnace, checked thermostat and verified operation, checked 16x25x4 Honeywell filter, checked intake pipe, cleaned drain trap, cleaned flame sensor, cleared drain line, checked ohms on the igniter, inspected heat exchanger, checked gas pressure low and high fire, checked amperage on blower and inducer motor, took a temperature reading on return and supply, checked all wires, cleaned unit, everything is running great!
Quoted customer a new AC system.
Quoted customer a two stage furnace with media filter and AC system.
Quoted customer a Bryant ductless heat pump system.
Just replaced a High limit switch on a Lennox furnace, cycled unit everything is running great!
Just completed a maintenance agreement furnace tune up on a Trane, checked thermostat and verified operation, checked and replaced Honeywell filters checked intake pipe, checked blower capacitor, cleaned drain trap, cleaned flame sensor, cleared drain line, checked ohms on the igniter, inspected heat exchanger, checked gas pressure low and high fire, checked amperage on blower and inducer motor, took a temperature reading, checked wires, cleaned unit, everything is running great!