Since 1995, First Call Heating & Cooling, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the Racine area. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that First Call Heating & Cooling, Inc. stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Kenosha, WI. Call us today at (262) 634-9025!
Service rep was very professional and provided a summary of the work provided. Great job thank you!!
I think she is a great asset to your team.
The technician came earlier ( but called 1st because he was ahead of schedule). Very clean and even wore the booties over his shoes!
Quick, clean and very professional
We have used First Call for years, and really love it. They are honest and respectful. We also appreciate knowing now that they give a veterans discount, and respect veterans.
Andrew was here from First Call Heating and checked out my furnace. He also changed the filter. Quick and efficient! Thank you.
The service agent didn't waist time. Found the trouble and fix the unit ASAP. I have Andrew back anytime. Great guy explained everything he did.
I can’t say enough about you guys I would never go anywhere else you really go above and beyond to take care Of my heating and cooling .
Our tech was awesome. Nicest guy ever. And he was good at his job too. Appreciated him coming out and checking on the furnace.
For safety all technicians should have a flashlight and eye protection goggles, which I supplied for this service.
Trane ac tuneup, maintenance, and inspection. Checked thermostat, checked air filter, checked blower, fan, and compressor amperage, checked temperature levels, checked refrigerant levels, checked capacitor, cleared drain line, cleaned condenser coils, checked contactor and all electrical connections, and verified unit operation. System running and cooling well!
Quoted customer a 2 stage furnace with AC system.
Armstrong furnace not heating due to a failing inducer motor, and sticking gas valve. Heat exchanger face plate is also rusted through. Due to age, potential cost of repairs, and condition, recommended replacement vs repair. Customer is rescheduled for free estimate
Boiler installation repair and service
Bryant ac tuneup, maintenance, and inspection. Checked thermostat, checked air filter, checked blower, fan, and compressor amperage, checked temperature levels, checked refrigerant levels, checked capacitor, cleared drain line, cleaned condenser coils, checked contactor and all electrical connections, and verified unit operation. System running and cooling well! Also installed new WiFi thermostat per customers request!
Commercial refrigeration and air conditioning repair service and installation
Just performed a furnace and a/c maintenance on a carrier system
Trane Ac tuneup, maintenance, and inspection. Checked thermostat and verified operation, checked air filter, cleared drain line, checked blower amps, checked temperature drop, checked line set insulation, checked all wire and electrical connections in blower compartment, cleaned condenser coils and unit, checked refrigerant levels, checked capacitor, checked contactor and verified voltage, checked all wire and electrical connections inside condenser, checked compressor and fan motor amperage. System running and cooling well !
Trane furnace heating intermittently due to a dirty flame sensor. Pulled and cleaned rod; cycled unit multiple times with no further issues present! Also checked air filter, blower and inducer motor amp draws, thermostat, temperature readings, wire connections, ignitor, and blower capacitor. Customer joined annual preventative maintenance plan with First Call!
Just performed a tune up on a Trane furnace
Quoted customer a 16 seer AC system.
Quoted customer a 2 stage furnace with media filter and wi-fi thermostat. Are adding a 16 seer AC system.
Quoted customer a new AC system.
Goodman furnace repair service and installation
Just completed a maintenance agreement tune up on a Goodman furnace, checked thermostat and verified operation, checked and replaced 16x20x1 filter, inspected flue pipe, checked blower capacitor, cleaned flame sensor, cleared drain line, checked ohms on the igniter, inspected heat exchanger, checked gas pressure, checked amperage on blower and inducer motor, took a temperature reading on return and supply, checked all wires, cleaned unit, everything is running great!