Since 1995, First Call Heating & Cooling, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the Racine area. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that First Call Heating & Cooling, Inc. stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Greendale, WI. Call us today at (262) 634-9025!
Great service. Very satisfied
Just completed a maintenance agreement tune up on a Trane XV95, Checked thermostat, checked filter, checked humidifier pad, moved damper to winter, checked intake pipe, cleaned flame sensor, cleaned drain trap, cleared drain line, inspected heat exchanger, checked ohms on igniter, checked gas pressure on low and high fire, checked amperage on blower and inducer motor, took a temperature reading of return and supply, checked wiring, cleaned unit everything is running great!
Rheem ac repair inspection maintenance tuneup replacement
Furnace tune up, furnace diagnostic service, trane furnace tune up, electronic air cleaner service, humidifier check
Complete furnace tune up on a Trane furnace. Replacement of 16x25x1 filter and adjustment of gas pressure at the gas valve in the furnace.
Followed up on AC install.
Air conditioning repair
Quoted customer a Trane AC system.
Complete furnace tuneup on train heating system. All mechanicals are in working order. Notice a slight humming noise coming from inducer sounds to be a bering sound. Notify customer of condition of motor rest of system.
Complete Rheem AC tune up complete at this time. Contactor showing wear advised customer of system condition. AC running at this time
Luxaire FL9 series furnace not heating properly. Only one burner lighting out of three. Pulled burner assembly cleaned out also clean flame sensor check the heat exchanger put unit back together and cycle furnace seems to be running at this time.
Two-stage variable speed trane furnace tuneup completed at this time per service plan. All mechanicals are in good working order at this time