In the Racine area, First Call Heating & Cooling, Inc. is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with First Call Heating & Cooling, Inc. because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Greendale, WI in Racine WI. Call us today at (262) 634-9025!
Service call as described, arrived within the 1 hour time frame. Professional, courteous. Nice touch to wear the shoe covers when you enter a house.
Great service. Very satisfied
Furnace maintenance repair service and installation
Rheem ac tuneup, maintenance, and inspection. Checked thermostat, checked air filter, checked blower, fan, and compressor amperage, checked temperature levels, checked refrigerant levels, checked capacitor, cleared drain line, cleaned condenser coils, checked contactor and all electrical connections, and verified unit operation. System running and cooling well!
Just completed a tune up on a Trane ac
Just completed a maintenance agreement furnace tune up on a Trane XB, Checked thermostat and verified operation, checked 16x25x4 Honeywell filter, checked intake pipe, checked blower capacitor, cleaned drain trap, cleaned flame sensor, cleared drain line, inspected heat exchanger, checked ohms on the igniter, checked amperage on blower and inducer motor, checked and adjusted gas pressure, took a temperature reading, checked all wires, cleaned unit, everything’s running great!
Just completed a furnace tune up on a Trane XR90, Checked thermostat and verified operation, checked 16x25x1 filter, checked intake pipe, checked blower capacitor, cleaned drain trap, cleaned flame sensor, cleared drain line, inspected heat exchanger, checked ohms on igniter, checked gas pressure low and high fire, checked amperage on blower and inducer motor, took a temperature reading on the return and supply, checked all wires, cleaned unit, everything is running great!
Just completed a maintenance agreement tune up on a Trane XV95, Checked thermostat, checked filter, checked humidifier pad, moved damper to winter, checked intake pipe, cleaned flame sensor, cleaned drain trap, cleared drain line, inspected heat exchanger, checked ohms on igniter, checked gas pressure on low and high fire, checked amperage on blower and inducer motor, took a temperature reading of return and supply, checked wiring, cleaned unit everything is running great!
Rheem ac repair inspection maintenance tuneup replacement
Furnace tune up, furnace diagnostic service, trane furnace tune up, electronic air cleaner service, humidifier check
Complete furnace tune up on a Trane furnace. Replacement of 16x25x1 filter and adjustment of gas pressure at the gas valve in the furnace.
Followed up on AC install.
Air conditioning repair
Quoted customer a Trane AC system.
Complete furnace tuneup on train heating system. All mechanicals are in working order. Notice a slight humming noise coming from inducer sounds to be a bering sound. Notify customer of condition of motor rest of system.
Complete Rheem AC tune up complete at this time. Contactor showing wear advised customer of system condition. AC running at this time
Luxaire FL9 series furnace not heating properly. Only one burner lighting out of three. Pulled burner assembly cleaned out also clean flame sensor check the heat exchanger put unit back together and cycle furnace seems to be running at this time.
Two-stage variable speed trane furnace tuneup completed at this time per service plan. All mechanicals are in good working order at this time