Since 1995, First Call Heating & Cooling, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the Racine area. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that First Call Heating & Cooling, Inc. stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Cudahy, WI. Call us today at (262) 634-9025!
Just Completed a central air tune up and cleaning including but not limited to, Check amp draw on compressor and fan motors, check all electrical connections, check contactor condition, check voltage to outdoor unit, inspect control wiring, clean outdoor coil and cabinet, check thermostat operation and batteries, Check indoor blower motor amp draw and condition, Check refrigerant (freon) level, Check reversing valve, clear drain lines and fittings, and cycle unit to verify operation. All where applicable. A/c is running and cooling good at this time!
Furnace repair service and installation
Trane furnace tuneup, maintenance, and inspection. Checked thermostat, cleaned condensate trap, checked air filter, cleared drain lines, cleaned flame sensor, checked igniter, inspected burners and heat exchanger, checked and cleaned intake pipe, checked blower and inducer motor amps, checked and adjusted gas pressure, checked all wire and electrical connections, checked temperature rise, and cleaned unit. System running and heating well!
Trane Ac check wanted due to hearing a strange noise. Checked air filter, cleared drain lines and fitting, checked temperature drop 20 degrees, checked indoor wire connections, checked outdoor capacitor 38/5.2 and rated for 40/5, contacts good, all wire connections in condenser good, all amp draws good, condenser coils clean, found no issues present today.
Trane central air conditioning repair maintenance and installation
Ac tuneup on trane air conditioner, checked thermostat, replaced airfilter, took amp draw on blower motor, checked all electrical connections, cleared drain lines, temperature drop, checked capacitor, and contactor. Took amp draw of fan and compressor, checked 410a refrigerant levels, inspected line set, and cleaned condenser coils
Bryant ac repair inspection maintenance tuneup
Quoted customer a new 16 seer cooling system.
Quoted customer a new air handler and AC system.
Installation of Lennox furnace
Heating and cooling, furnace diagnostic, furnace repair, heating repair, Hvac repair, tempstar furnace repair Hvac, heat exchanger
Trane furnace maintenance
Concord ac repair inspection maintenance
Ac tune up on trane cooling unit. Replacing or cleaning air filters as to manufacturers specifications is key to the proper operation of the system
Trane ac repair inspection maintenance
Installed Trane XC95 modulating variable speed high efficiency gas furnace. Also installed Trane whole house humidifier. New Trane XL950 thermostat with wifi control operating system great.