In the Racine area, First Call Heating & Cooling, Inc. is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with First Call Heating & Cooling, Inc. because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace, Heat Pump, & AC Repair in Burlington, WI. Call us today at (262) 634-9025!
Brian Wolf was amazing, professional, and friendly as can be! Myself and family are definitely recommending neighbors to First Call. The whole process exceeded expectations thanks to Brian!
Awesome experience.. Glad i signed up for the maintenance program
Our central air stopped working and the technician was very friendly and knowledgeable. He was able to complete the repair in one visit the house is nice and cool again.
Low voltage wire was repaired. Dog chewed up wiring
Installed new hot water heater
Ran unit for 15 min to try and narrow down. Leak, found center of evap pan small leak onto furnace. Found txv distributor lines overhanging evap pan causing condensation drip. Bent txv line in closer to evap coil, re connected duct work and tested. No leaks at this point. Informed customer of situation. Called office for verifying warranty, call will be under warranty With no charge to customer..
Quoted customer new AC unit.
Quoted customer a 16 seer AC system.
Bryant furnace tuneup, maintenance, and inspection. Checked thermostat, cleaned condensate trap, checked air filter, cleared drain lines, cleaned flame sensor, checked igniter, inspected burners and heat exchanger, checked and cleaned intake pipe, checked blower and inducer motor amps, checked and adjusted gas pressure, checked all wire and electrical connections, checked temperature rise, and cleaned unit. System running and heating well!
Found furnace running and heating fine hen arrived. Changed service call into tuneup as there were no obvious issues. Did recall error through main board and saw error 32, low heat pressure switch did not close. However could not get furnace to fault when on site. Completed tuneup and looked over pressure switch hoses and connections. Also found GV throttle valve wires had fallen off. Re attached and tested. Checked thermostat and verified operation, Ok checked air filter, New cleaned condensate trap, cleared drain lines, inspected burners and heat exchanger, Slow to light but lighting fine. cleaned intake pipe, cleaned flame sensor, checked ignitor, 63 ohms, fine checked blower and inducer motor amperage, .5/.3 checked gas pressure, .6/1.5/3.2 checked temperature rise, 40/65 low and medium/ high checked all wire and electrical connections, and cleaned unit. Unit running and heating well!
Just performed service on a Trane air conditioner
Heating cooling refrigeration repair service and installation
Quoted customer a modulating furnace with 16 seer AC system.
Just performed two furnace inspections
Furnace repair service and installation